In the Denton County Area, Strittmatter Heating & Air and Plumbing is well known for providing exceptional ac repair, installation, and service. The people we send out to serve you are also top notch, something you'll see in their reviews below. Everyone you deal with at our company has the goal of making sure your experience with us will be so good you'll call us every time you need help. You can feel confident working with Strittmatter Heating & Air and Plumbing because we stand behind our work and comply with all local codes. This is why, as you can see by the map and reviews below, we are rated so highly for AC, Furnace, and Plumbing Repair in Bartonville, TX in Denton TX. Call us today at (940) 566-1122!
We appreciate the prompt assistance, professional service, and honest evaluation.
Everything was explained very well and service was great!
Tuneup on a 16 seer 2 stage Goodman heat pump and found the unit running well and cooling efficiently. Cleaned a few components and it is cooling like a champ. Call Strittmatter’s today to schedule your appointment.
Cleaned tub drain branch line.
Quote to install customer provided carbon filter in garage.
Pulled and reset toilet
Replace expansion tank 50 gallon gas water heater in installed new vacuum breaker at hose bib
Replaced fill valve in master toilet
Cleaned sewer line
Did tune up on two Carrier systems. All operations were normal. Recommended air scrubbers, surge protection on air handlers and heat pumps. And condensate drain protection.
Did tune up on four systems. Cleared drain lines and changed all filters. All system operations were normal.
Checked system and found bad primary circuit board. Replaced board and tested system and all operations returned to normal.
Installing whole house water softener
Disconnect kitchen sink for new countertops
Fall tuneup on 4 lennox gas systems and 1 Carrier heat pump system and found some small issues but overall systems are running well and heating as designed!
Did fall tune up on 4 systems. Recommended air scrubber and condensate drain protection.
Fall tune ups
Went out to give customer bid to replace one system and ducts to new addition.
Checked System and found blower motor not communicating with primary circuit board. replaced primary circuit board and all operations returned to normal.
Made minor wire repair to outdoor unit, condenser fan motor was spinning the wrong direction and was running unit inefficiently until it was possibly overheating and shutting down compressor. After making repairs unit resumed normal function and is cooling as designed.
Capped outside shower valve and took it out of wall.
Spring Tune up
Spring Tune up
Installed air scrubber plus
Spring Tune up on Heat Pump System.
Added cold water line and hose bib at feed store.